[time-nuts] Wine cooler as temperature chamber
jimlux at earthlink.net
Tue Oct 14 13:47:04 UTC 2014
On 10/14/14, 6:13 AM, Chuck Harris wrote:
> Uhmm? How does that differ from any heat pump, such as say, a freon
> cycle refrigerator?
The COP for thermoelectric coolers (heat moved vs power consumed),
particularly at large delta T, is fairly poor, compared to heat pumps.
A heat pump might take 1 watt to move 5 watts, while a TEC might take 5
watts to move 1 watt.
> The biggest problem with Peltier coolers is they have a very low
> thermal resistance shunt (all of the thermocouple junctions) between
> the hot side and the cool side. If you turn them off, the hot and
> cool side will equilibrate almost instantly.
TECs are great for rapid adjustments of small delta T.
> Not very efficient!
> You can, however, make large stacks of Peltier coolers, hot to cool,
> and cool them down to liquid air temperatures. This is done on
> very low noise LNA's.
I've seen stacks of 5 TECs that look like a ziggurat for this kind of
There's a problem with trading off the "incremental power" as you go
warmer (e.g. the tip of the pile sucks out 0.1 W and dissipates 1W, then
the next sucks up 1W and dissipates 10W, then the next unit has to
absorb 10W and dissipate 100W, etc.
> -Chuck Harris
> Chris Albertson wrote:
>> The worst thing about those small refrigerators is that were NEVER
>> to cool objects that PRODUCE heat. A wine bottle does not burn any
>> electrical power. If you place even the smallest heat producing
>> electrical device inside the cooler it is going to have to pump out
>> whatever heat is being generating just to keep equal temperature with the
>> room's ambient temperature.
>> So you place some small device that uses 500ma at 12V and you have a 6W
>> heater. It will requires more than 6W of cooling power just to keep
> time-nuts mailing list -- time-nuts at febo.com
> To unsubscribe, go to
> and follow the instructions there.
More information about the Time-nuts_lists.febo.com